Instructions for interfacing the Turner Designs Cyclops-7 with a NexSens iSIC data logger:
IMPORTANT: Review the manufacturer’s manual for the sensor to ensure that the sensor is properly configured for integration with a third party data logger prior to connecting the device to the iSIC.
1. Route cables and wires through one of the gland fittings installed on the iSIC enclosure.
2. Unplug the green terminal strip from the iSIC before inserting sensor wiring. The left terminal strip is designated for digital inputs (RS-485, RS-232, SDI-12, etc.) ; the right for analog inputs (mV, 4-20 mA, etc.).
3. Connect the sensor wires to the terminal strip as shown in the diagram below.
IMPORTANT: Verify that no wires are loose or clamped on the insulation as this will cause intermittent or failed communication. Seal and caulk the gland fitting to prevent moisture intrusion and maintain the NEMA4X rating of the iSIC enclosure.
- Keep the resistors as close to the iSIC terminal as possible. The best location is right on the iSIC terminal.
- when more than one analog sensor is attached AD1, AD2, … , AD7 must be utilized.