|Temperature data is displayed as a value between -99999 and -100001
|Modbus address of sensor node is different than the queried address.
|Connect a single node and query its temperature using the universal address of 251.
|Use a DVM to verify power is getting through to the receptacle (bottom) port of the final node on the string. Measurement between Pins 4 and 7 must be 5-24V.
|String disconnected or incorrect wiring.
|Inspect the string’s connection to the DCP. Switch the sensor’s RS485A and RS485B leads (naming convention is not standardized acrossed devices).
|Water ingress into one or more cable/sensor connections on the string.
|Inspect cable and sensor plug and receptacle O-rings. If necessary, clean connector pins with 91% Isopropyl Alcohol and Q-tips and dry with compressed air.